Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||15 July 2005|
|PDF File Size:||6.53 Mb|
|ePub File Size:||20.93 Mb|
|Price:||Free* [*Free Regsitration Required]|
Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided um01 this product. Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that’s contained in this manual.
Loosen the terminal screw and route the wires through the opening in the o cover. Remove the mounting template. You must also provide an acceptable grounding path for each device in your application.
Tighten the terminal screw, making sure the pressure plate secures the wire.
IN – Rockwell Automation
You must provide a Customer Support case number call the phone number above to obtain one to your distributor in order to complete the return process. Replace the cover as shown below.
Hook the top slot over the DIN rail. Failure to remove strip before operating can cause overheating. New Product Satisfaction Return Rockwell Automation tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. Industrial Automation Wiring and Grounding Guidelines Mount your DIN rail. Unhook the top of the DIN rail slot from the rail.
Output group to output group isolation Verified by one of the following dielectric tests: Switching inductive loads without surge suppression can significantly reduce the life of relay contacts or damage transistor outputs.
Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation.
Repeat steps 1 and 2 for the second DIN rail latch. Without appropriate precautions, there may be potential difficulties ensuring electromagnetic compatibility in other environments due to conducted as um00 as radiated disturbance. Documents Flashcards Grammar checker. When using spade lugs, use a small, flat-blade screwdriver to pry the finger-safe cover from the terminal blocks, then loosen the terminal screw.
Scripting must be enabled to use this site.
For AC-powered controllers, this connection must be made for safety purposes. The Belden cable has two signal wires black and clearone drain wire, and a foil shield. MicroLogix Instruction Set Reference Manual RM A reference manual that contains data and function files, instruction set, and troubleshooting information for MicroLogix Once wiring is complete, be sure the controller is free of all metal fragments before removing the protective debris strip.
It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts. For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs.
Follow these steps to connect the replaceable battery. Use a power supply that matches the transmitter specifications as shown. Wire the Controller The shading in the following terminal block illustrations indicates which terminal groups are tied to which commons.
Refer to the mounting template inside the back cover of this document. See UL File E The analog output can support a voltage function as shown in the following illustration.
This could cause an explosion in hazardous location installations. Output 2, 3 and 4 may be used like the other FET transistor outputs, but in addition, within a limited current range, they may be operated at a higher speed. Linea centrale della guida DIN.
This equipment is supplied as open-type equipment. Install your controller using these installation instructions. Each 176 is supplied with markings on the rating nameplate indicating the hazardous location temperature code.